① Thoroughly clean the bottom surface and install the heating insulation without any gaps.
At this time, install the edge with 5 cm distance from the wall. Tape the joints of heat insulation.
② Arrange the GT Carbon Heating on the insulation at intervals of 50-150 mm and space them 5 cm apart from the edges of the insulation (with 10 cm distance from the wall).
③After wiring the GT Carbon Heating in series or parallel, the joints are thoroughly double-waterproofed with heat shrink tubing and butyl tape.
④ Connect the electricity to the thermostat to check if there is disconnection or whether it is operated properly.
⑤Inspect the installation interval of GT Carbon Heating, joints, connection of wires to check whether there is any abnormality.
⑥In the case of wide space or multiple use facilities, place mesh (iron mesh or drivit for floor) and mortar (at client's expense) at a thickness of about
2.5~3.5 cm to maintain smoothness (3~3.5 cm for floor mortar, and maintain 2.5 cm or over in the case of hand plastering to minimize cracks)
* Plastering is not in the range of heating work
⑦ After a complete dry (3 to 5 days), connect the heat for at least one day to dry moisture within the mortar before installing finishing materials.
※Double-waterproof finish with butyl tape is recommended after a heat shrink tube operation